## Posts Tagged ‘electrical generator’

### Boiler Feed Pumps Experience Cavitation

Wednesday, January 3rd, 2018
 Shortly after I graduated with my engineering degree I worked as a power plant engineer at an electric utility.   One day I was walking through the plant and heard a loud racket coming from the boiler feel pumps.   These are the massive centrifugal pumps that deliver pressurized water to the boiler.   The water is transformed into steam to drive steam turbines and spin electrical generators, which ultimately results in electrical power.   The noise was so loud, it sounded like rocks were being ground up.   I asked a coworker what was going on, and he replied matter-of-factly, “The pumps are cavitating.” Boiler Feed Pumps Experience Cavitation         So what exactly is cavitation?   We’ll find out next time when we explore the mechanics of this noisy phenomenon as it applies to boiler feed pumps and other centrifugal pumps. opyright 2017 – Philip J. O’Keefe, PE Engineering Expert Witness Blog ____________________________________

### Enthalpy and Steam Turbines

Thursday, November 14th, 2013
 Last time we learned how the formation of condensate within a power plant’s turbine results in a vacuum being created.   This vacuum plays a key role in increasing steam turbine efficiency because it affects a property known as enthalpy, a term used to denote total heat energy contained within a substance.   For the purposes of our discussion, that would be the heat energy contained within steam which flows through the turbine in a power plant.       The term enthalpy was first introduced by scientists within the context of the science of thermodynamics sometime in the early 20th Century.   As discussed in a previous blog article, thermodynamics is the science that deals with heat and work present within processes.   Enthalpy is a key factor in thermodynamics, and is commonly represented in engineering calculations by the letter h and denoted as, h = u + Pv where u is the internal energy of a substance, let’s say steam; P is the pressure acting upon a specific volume, v, of the steam; and P and v are multiplied together.   Pressure is force per unit area and is measured in psi, pounds per square inch.   For the purposes of our discussion, it’s the amount of pressure that steam places on pipes containing it.       Looking at the equation above, simple math tells us that if we increase the pressure, P, the result will be an increase in enthalpy h.   If we decrease P, the result will be a decrease in h.   Now, let’s see why this property is important with regard to the operation of a steam turbine.       When it comes to steam turbines, thermodynamics tells us that the amount of work they perform is proportional to the difference between the enthalpy of the steam entering the turbine and the enthalpy of the steam at the turbine’s exhaust.   What is meant by work is the act of driving the electrical generator, which in turn provides electric power.  In other words, the work leads to a useful outcome.   This relationship is represented by the following equation, W = h1 – h2       In terms of the illustration below, W stands for work, or potential for useful outcome of the turbine/generator process in the form of electricity, h1 is the enthalpy of the steam entering the inlet of the turbine from the superheater, and h2 is the enthalpy of the steam leaving at the turbine exhaust.       We’ll discuss the importance of enthalpy in more detail next week, when we’ll apply the concept to the work output of a steam turbine. ________________________________________

### Superheater Construction and Function

Sunday, September 15th, 2013
 Power plants produce electrical energy for consumers to use, whether at home or for business, that’s obvious enough, but did you know that in order to produce that electrical energy they must first be supplied with heat energy?   The heat energy that power plants crave comes from a fuel source, such as coal, oil, or natural gas, by way of a burning process.   Once the heat energy is released from the coal through burning, it’s transported into a steam turbine by way of superheated steam, which is supplied to it by a piece of equipment named, appropriately enough, a superheater.       So what is a superheater and how does it function?   Take a look at the illustration below.       The superheater looks like a W.   It’s actually a cascading array of bent steam pipe, situated above a source of open flames which are produced by the burning of a fuel source.   A photo of an actual superheater is shown below.       So how many bends are in a superheater?   Enough to fill the needs of the particular power plant it is supplying energy to.   Since all power plants are designed differently, we’ll keep things in general terms.       The many bends in the superheater’s pipes form a circuitous path for steam to flow as it follows a path from the boiler to the steam turbine.   The superheater’s unique construction gives the steam flowing through it maximum exposure to heat.   In other words, the bends increase the time it takes for the steam to flow through the superheater.   The more bends that are present, the longer the steam will be exposed to the flame’s heat energy, and the longer that exposure, the more heat energy that is absorbed by the steam.       Superheating routinely results in temperatures in excess of 1000°F.   This superheated steam is laden with abundant heat energy which will keep the steam turbine spinning and the generator operating.   The net result is millions of watts of electrical power.       As we learned in a previous blog, the superheater is designed to provide the turbine with sensible heat energy to prevent steam from completely desuperheating, which would result in dangerous condensation inside the turbine.       The newly added superheater is a major improvement to a power plant’s water-to-steam cycle, but there’s still plenty of waste and inefficiency in the system, which we’ll discuss next week. ________________________________________

### Superheating, Part I

Monday, August 19th, 2013
 Last time we learned that our power plant boiler as presently designed doesn’t do a good job of producing ample amounts of superheated steam, the kind of steam that turbines need to spin and power generators.   During the process of superheating the more heat energy that’s added to the steam in our boiler, the higher its temperature becomes.   However, our boiler can only produce a limited amount of superheated steam as it stands now.       So how do we get more heat energy into the superheated steam?   Take a look at the illustration below for the solution to the problem.       You’ll note a prominent new addition to our illustration.   It’s called a superheater.       The superheater performs the function of raising the temperature of the steam produced in our boiler to the incredibly high temperatures required to run steam turbines and electrical generators down the line, as explained in my blog on steam turbines.   The superheater adds more heat energy to the steam than the boiler can alone.       In fact, the amount of heat energy in the superheated steam produced with our new design is proportional to the amount of electrical energy that power plant generators produce.   Its addition to our setup will result in more energy supplied to the turbine, which in turn spins the generator.   The result is more electricity for consumers to use and a more efficiently operating power plant.       But inefficiency isn’t the only problem addressed by the superheater.   We’ll see what else it can do next week. ________________________________________

### Heat Energy Within the Power Plant— Water and Steam Cycle, Part 2

Wednesday, August 14th, 2013
 Last time we learned that electric utility power plants must have water treatment systems in place to remove contaminants from incoming feed water before it can be used.   This clarified water is then fed to a boiler by the boiler feed pump as shown below.       As it stands this setup will work to provide electricity, however in this state it’s both inefficient and wasteful.   We’ll see why in a minute.       Boilers, as their name implies, do a great job of heating water to boiling point to produce steam.   They do this by adding the heat energy produced by burning fuel, such as coal, to water, then steam.   We learned in earlier blogs in this series that the energy used to heat water to boiling point temperature is known as sensible heat, whereas the heat energy used to produce steam is known as latent heat.   The key distinction between these two phases is that during sensible heating there is a rise in temperature, during latent heating there is not.   For a review on this, see this blog article.       When water starts to heat inside the boiler, sensible heat energy is said to be added.   This is represented by phase A of the graph below.       During A, heat energy will raise the temperature of the water to boiling point.   As the water continues to boil in phase B, water is transforming into steam.   During this phase latent heat energy is said to be added, and the temperature will remain at boiling point.       In phase C something new takes place.  The temperature rises beyond boiling point and only steam is present.   This is known as superheated steam.   For example, if the boiler pressure is at 1,500 pounds per square inch, steam becomes superheated at temperatures greater than 600°F.       Unfortunately, boilers alone do a poor job of superheating steam, that is, continuing to raise the temperature of the steam present in phase C.   This is evident by the fact that phase C is quite small in comparison to phases A and B before it.   This inefficiency in producing ample amounts of superheated steam results in a small amount of useful energy being provided to the turbine down the line, which is bad, because steam turbines require exclusively superheated steam to run the generator.       Next time we’ll see how to provide our steam turbine with more of what it needs to run the generator, more superheated steam. ___________________________________________

### Coal Power Plant Fundamentals – The Generator

Monday, March 7th, 2011
 When I was a kid I remember how cool it was to have a headlight on my bike.  Unlike the headlights that the other kids had, mine was not powered with flashlight batteries.  The power came from a little gadget with a small wheel that rode on the front tire.  As I pedaled along, the tire’s spinning caused the small wheel to spin, and voila, the headlight bulb came to life.  Little did I know that this gadget was a simple form of electrical generator, and of course I was oblivious to the fact that a similar device, albeit on a much larger scale, was being used at a nearby power plant to send electricity to my home.      Over the last few weeks we learned how a coal fired power plant transforms chemical energy stored in coal into heat energy and then into mechanical energy which enables a steam turbine shaft to spin.  We’ll now turn our attention to the electrical generator.  It’s responsible for performing the last step in the energy conversion process, that is, it converts mechanical energy from the steam turbine into the desired end product, electrical energy for our use.  It represents the culmination in energy’s journey through the power plant, the process by which energy contained in a lump of coal is transformed into electricity.        To show how this final energy conversion process works, let’s look at Figure 1, a simplified illustration of an electrical generator. Figure 1 – A Basic Electrical Generator      You’ll note that the generator in our illustration has a shaft with a loop of wire attached to it.  When the shaft spins, so does the loop.  The shaft and wire loop are placed between the north (N) and south (S) poles of a horseshoe magnet.  It’s a permanent magnet, so it always has invisible lines of magnetic flux traveling between its two poles.  These magnetic lines of flux are the same type as the ones created by kids’ magnets, when they play with watching paperclips jump up to meet the magnet.  The properties of magnets are not completely understood, even to adults who work with them every day.  And what could be more mysterious than the fact that as the shaft and wire loop spin through the lines of magnetic flux in the generator, an electric current is produced in the wire loop.      Now, this current that’s flowing through the spinning wire loop is of no use if we can’t channel it out of the generator.   The wire loop is spinning vigorously, so you can’t directly connect the ends of the loop to stationary wires.  A special treatment is required.  Each end of the loop is connected to a slip ring.  A part called a “brush” presses against each slip ring to make electrical contact.  The electrical current then flows from the loop through the spinning slip rings, through the brushes, and into the stationary wires.   So, if, for example, a light bulb is connected to the other end of the stationary wires, this completes an electric circuit through which current can flow.  The light bulb will glow as long as the generator shaft keeps spinning and the wire loop keeps passing through the magnetic lines of flux from the magnet.      So we see that the key to the whole energy conversion process is to have movement between magnetic lines of flux and a loop of wire.  As long as this movement occurs, the electricity will flow.  This basic principle is the same in a coal fired power plant, but the electrical generator is far more complicated in construction and operation than shown here.  My Coal Power Plant Fundamentals seminar goes into far greater detail on this and other aspects of electricity generation, but what I have shared with you above will give you a basic understanding of how they operate.      That concludes our journal with coal through the power plant.  This series of blogs has, you will remember, presented a simplified version of the complex material presented in my teaching seminars.  Next week we’ll branch off, taking a look at why electrical wires come in different thicknesses.    _____________________________________________

### Coal Power Plant Fundamentals – The Steam Turbine

Sunday, February 20th, 2011